Available Fault-Current Calculation and Protection: Page 2 of 2
Inside this Article
Ampere Interrupting Capacity
Once you determine the available fault current, you can select appropriately rated circuit breakers or fuses. There are two basic short-circuit protection systems: fully rated systems, which you must selectively coordinate in certain circumstances (see “Selective Coordination of OCPDs,” p. 16), and series-rated systems. As long as you use a listed circuit breaker (UL 489) or fuse (UL 248) in accordance with its ampere interrupting capacity (AIC) and voltage rating or in accordance with its listing as part of a series-connected system, a Nationally Recognized Testing Laboratory (NRTL) has verified its ability to clear a fault without extensive damage to the equipment or electrical system.
Fully rated system. Designing and deploying a fully rated system is relatively straightforward. Listed OCPDs are certified to and marked with an AIC, which identifies the maximum available fault current the device is rated to withstand on its own. These AIC ratings step up in standard increments, such as 10K, 18K, 22K, 25K, 35K, 42K, 65K, 100K and 200K. Listed panelboards, meanwhile, are marked with a short-circuit current rating (SCCR), which is the maximum current the component or assembly can withstand.
In a fully rated system, each OCPD device has an AIC rating that is greater than or equal to the available fault current. Moreover, the piece of equipment in the assembly with the lowest interrupt rating determines the full rating for a panelboard with circuit breakers installed. As an example, the equipment configuration in Figure 1 would have a full rating of 22K amperes—even though the panelboard and main breaker are rated for 65K amperes—as determined by the lowest-rated piece of equipment or OCPD, which in this instance is a branch circuit breaker.
You must design an electrical system with a single OCPD as a fully rated system. If you are designing an electrical system with multiple OCPDs, however, a series-rated system may provide the best value, which is an important consideration for your customers.
Series-rated system. The NEC allows the available short-circuit fault current to exceed the AIC rating of an OCPD under certain circumstances, as detailed in 240.86, Series Ratings. As described in the NEC Handbook, a series-rated system is “a combination of circuit breakers or fuses and circuit breakers that can be applied at available short-circuit levels above the interrupt rating on the load-side circuit breakers but not above the main or line-side device.” This arrangement is allowed for tested combinations of equipment [240.86(B)] or under engineering supervision in existing installations [240.86(A)]; it is not allowed with certain motor-load levels or configurations [240.86(C)].
The most common way to design and deploy a series-rated short-circuit protection system is to use tested equipment combinations, which are combinations of OCPDs that have passed NRTL product safety and certification tests as an assembly. In a series-rated system, only the first OCPD needs to be AIC rated for the full available fault current. Downstream series-connected devices may have a lower AIC rating, provided that an NRTL has shown that the series-connected assembly works together to clear a fault and protect the electrical equipment from damage. If the main and branch circuit breakers in Figure 1 were part of a listed series-rated combination, then the assembly would be series rated for 65K amperes of fault current, as determined by the main breaker AIC rating and panelboard SCCR.
When using series-rated equipment, you must do so in a manner consistent with the product listing and the manufacturer’s instructions. The first step is to get your hands on the series-rating tables for equipment you would like to use. These tables are readily available online. UL maintains these data in tabular form, organized by manufacturer, and most manufacturers also publish their own tables, which must comply with UL standards. The UL or the equipment manufacturer may organize and present these data in a number of ways: by service voltage, by type of breaker or fuse, by equipment combination (breaker-breaker, fuse-breaker, triple-series rating) and so forth. Regardless of the method of data organization, you basically need to find the series combination that matches your design voltage, available fault current and OCPD capacity. The following example illustrates this process for a breaker-breaker combination.
Example of a tested series configuration: This scenario assumes an available fault current of 28,000 amperes at 480 Vac. If you would like to use a 3-phase 250 A Eaton panelboard, subject to the series equipment ratings in Table 1, then you need to look at the 35 kA column and the 250 A main breaker row to meet or exceed the available fault current at the desired capacity level. According to the highlighted cell, you may use a JD- or JDB-type main breaker in series with GHB-type branch circuit breakers. However, this series rating only applies if all the branch circuit breakers in the panelboard are rated between 15 A and 50 A. To accommodate a GHB-type branch circuit breaker rated for more than 50 A, you would need to step up to the 65K A column, which calls for a HJD-type main breaker.
In existing installations, the Code also allows a licensed professional engineer (PE) to select series-rated devices. In these calculated applications, the PE must evaluate the time-current curves for the OCPDs and ensure that the downstream circuit breakers will remain passive (closed) when the upstream device clears the available fault current. In addition to performing manual calculations, a PE can also use specialized software tools as a means of selecting appropriate devices.
Note that product safety standards require specific markings for panelboards and switchboards that a NRTL has investigated and approved for use in a series-rated system. These markings identify allowable combinations of integral and remote OCPDs, which you must observe to maintain the panelboard’s marked SCCR. Furthermore, NEC Section 110.22 includes identification requirements for equipment enclosures with series-rated devices. Installers must field-identify these labels with the effective series-connected protection rating, as directed by a PE or the equipment manufacturer. To maintain this level of protection, the label must also state that identified replacement components are required.
—Ben Bachelder / Sun Light & Power / Berkeley, CA / sunlightandpower.com